Retire el ATV del embalaje y compruebe que no presenta daños. .. Consulte el manual del programación (BBV) para una descripción completa del. Manual de programación Altivar® 06/ Contenido .. Altivar 31 (ATV31) es una familia de variadores de velocidad de ~ (c.a.) de frecuencia ajustable. Manual de programación. ATV Manual de programación Manual de programación · altivar-machine-atv ATV Manual de programación.
|Published (Last):||21 September 2008|
|PDF File Size:||8.96 Mb|
|ePub File Size:||9.2 Mb|
|Price:||Free* [*Free Regsitration Required]|
Programacion de Variadores de Velocidad Altivar ATV312
Link 3 on the drive is then via the filter output cable. Assistance with maintenance, detected fault display If a problem arises during setup or operation, ensure that the recommendations relating to the environment, mounting and connections have been observed. Failure to follow these instructions can result in death, serious injury, or equipment damage.
For complete documentation, refer to www. We share information about your activities on the site with our partners and Google partners: Altivar Download PDF. This diagram is for the standard ATV products.
Derating curves are shown on page 15 as a function of switching frequency, ambient temperature and mounting conditions.
Simplified manual This manual is an extract from programming and installation manual. Shielded cable for motor connection with shielding connected to ground at both ends. The following Altivar technical documents are available on the Altivar – Botek Otomasyon B. The shielding must be continuous and intermediate terminals must be in EMC shielded metal boxes. Altivar 61 C1 EMC. If the installation includes several drives, provide one “residual current device” per drive.
Electrical equipment should be installed, operated, serviced, and maintained only by qualified personnel. Weight kg lb M3, M3 72 2. The high frequency equipotential ground connection between the drive, motor, and cable shielding does not eliminate the need to connect the ground PE conductors green-yellow to the appropriate terminals on each unit.
Mount the drive v Mount the drive in accordance with the instructions in this document see page Schneider Electric Altivar Drive – Grainger. Certain detected faults can be programmed for automatic restart after the cause has disappeared. Use a permanent insulation monitor compatible with non-linear loads for example Merlin Gerin type XM Find the cause of the detected fault and correct it.
EMC plate supplied with the drive, to be installed as indicated on the diagram. For control and speed reference circuits, we recommend using shielded twisted cables with a pitch of between 25 and 50 mm 1 and 2 in.
Do not place it close to heating elements. Please refer to the catalogue. If the cable is connected to equipment that may have a different ground potential, then ground maunal shield at one end only to prevent large currents from flowing in the shield.
Altivar – Sonepar www. Accidental grounding can result in unintended activation of drive functions. Your consent to our cookies if you continue to use this website. Altivar – Sonepar. The first fault detected is stored and displayed, flashing, on the screen: The shield can then be grounded at both ends. However, it is advisable to perform mwnual following checks regularly: Before starting up the drive, please check the following points regarding mechanical and electrical installations, then use and run the drive.
Variadores Schneider – Automatización y Control
Altivar Altivar Altivar – inverter – plc – otomasyon B. The temperature rise is controlled by a sensor in the power module.
Above 4 kHz, the drive will reduce the switching frequency in the event of excessive temperature rise. Check that the frequency defined by the frequency bFr the factory setting is 50 Hz is in accordance with the frequency of the motor. In this configuration EMC compliance is not guaranteed.
The detected fault will no longer be present if it’s cause has been corrected. This is dependant on the type of installation. Keep the control circuits away from the power circuits. No responsibility is assumed by Schneider Electric for any consequences arising out of the use of this product. Following a storage time between 2 and 3 years: Communication variables guide The Communication variables manual defines the drive control processes maanual the drive variables which can be accessed by the communication buses: Altivar V www.
To measure the DC bus voltage: Equipment Grounding Ground the drive according to local and national code requirements.
Obey all safety messages that follow this symbol to avoid possible injury or death. The Altivar drive is designed to make industrial and commercial machines. In the event of a non resettable detected fault: Branch circuit protection must be provided in accordance with the National Electrical Code and any additional local codes.
Altivar – Schneider Electric T1: Failure to follow these instructions can result in injury or equipment damage.